Gas & Oil Vents
It is essential that Gas and oil vents are installed to comply with Document J of the Building Regulations in England and Wales and Part F of the Building Regulations in Scotland, as well as to the flue manufacturer's installation instructions. In the UK the installation must also comply with BS5440 part 1:2000 for gas flues up to 60 kW. Only Gas Safe Register or OFTEC registered installers can commission the flue installation if the appliance is connected to the fuel supply.
Gas and Oil vents are manufactured, tested and approved to BS EN 1856 Part 1.
The Gas and Oil vent must remain as straight as possible and be of a height so as to ensure sufficient draught to clear the products of combustion (see termination details). Both gas and oil vents are extremely adaptable, but excessive changes of direction and angles greater than 45° from the vertical in any flue system must be avoided, as they create considerable resistance to the movement of the flue gases. Horizontal runs must never be used and the first section of the vent must rise 600mm vertically from the top of the appliance.
The vertical distance between the appliance and the flue termination should always be twice the angled distance between the appliance and termination. In accordance with the Building Regulations, a minimum of 50mm distance to combustibles must be maintained.
The Gas and Oil vents firestop/support components provide a 50mm clearance. At the maximum flue gas temperature of 250°C, the outer case will be in the region of 75-85°C Gas vent normally has an aluminium liner and a Zalutite outer skin with an air cavity, and can be used both internally and externally. However long external runs must be avoided and where external runs exceed 3 metres an insulated vent must be used. Oil vents have a stainless steel liner and are insulated. They are totally interchangeable with the Gas Vent without the need for adaptors.
Any galvanised components used externally should be suitably weather protected.
Within both ranges there are adjustable lengths which can be used to telescope over a standard pipe length to provide the exact flue lengths required. It should not be used directly after a bend since there is insufficient overlap to insure a sound joint. A wall band must be used above an adjustable length as this component is not load bearing.
Always use an appliance connector to connect to the appliance, sealed using fibre rope and fire cement or high temperature silicone sealant.
Internally run systems should be supported by using a support or ceiling support plate fixed on top of the floor/ceiling joists. Firestop plates are also required being fixed below the ceiling. Both components have purpose made lugs to ensure the 50mm distance to combustibles is maintained. Wall bands are not load bearing and give lateral support only. They should be fitted every 3m to ensure adequate support for the system. The maximum height unsupported above the roof line is 1.5m. Rigid stays or guy wires must be used if the installation terminates higher.
Use of an adjustable length immediately above the appliance enables removal of the appliance later without dismantling the full system.
Read our top tips for installers and consumers on stove safety while enjoying the great outdoors
Specflue's response to the new clean air strategy
Specflue's guide to getting your woodburner ready for the summer months.
More and more people who consider themselves ‘too posh to pitch’ are opting for a new way of camping that involves less effort and great…
The Department for Environment, Food & Rural Affairs (Defra) is seeking information on the use of fuels such as wood, house coal and manufac…
Specflue appoints Deborah McCreadie to Business Development Manager - Commercial Products
HETAS Technical note TN_0022
Specflue's Commercial Director, Ian Sams responds to Sadiq Khan's calls for a Wood-Burning Stove Ban in the capital.
As the air now carries an autumnal nip in the mornings and evening, it will not be long before we experience the first frosts of the season,…
Simple step by step guide on how to check your CO alarm is working correctly and prepare it for the coming heating season.
With just a few days until Christmas, most people should be well into their season of burning with their stoves and open fires. However, the…
Wood needs to dry out and allow the sap to evaporate out of the heart of the timber. Drying wood, although sounding a simple process, has a…
Follow these ten tips to ensure proper installation and avoid some common mistakes.
Schiedel have been manufacturing twin skin flexible liners at their Washington plant for over 40 years and are now proud to offer householde…
The popularity of wood burning appliances has risen in recent years, which means that heating engineers are more likely to be quizzed
While Britain is warming to the benefits of traditional wood burning stoves, Phil Lowe, Head of Sales and Marketing at Specflue, a leading s…