Twin Wall Chimney Systems
All twin wall chimney systems must be installed to comply with Document J of the Building Regulations in England and Wales and part F of the Building Regulations in Scotland, as well as to the flue manufacturer's installation instructions.
The twin wall chimney system should remain as straight as possible and be high enough to ensure sufficient draught to clear the products of combustion. The height necessary for this will depend upon the type of the appliance, the height of the building, and the number of offsets within the system. However, a minimum flue height of 4.5 metres should be achieved as recommended in the Building Regulations.
Where it is not possible to construct a vertical chimney, Building Regulations dictate that no part of a chimney should form an angle greater than 45° from the vertical, except where it may be necessary to use a very short horizontal section, not exceeding 150mm, of flue to connect the chimney to a back outlet appliance. The run between offsets should not exceed 20% of the overall height of the chimney. In both instances a maximum of two offsets in any one chimney run should be used. Cleaning access must be provided in chimney systems with two offsets. It is also a recommendation that a vertical rise of 600mm should be allowed, immediately above the appliance before any change of direction.
Where the chimney passes through a combustible floor or ceiling, an air gap clearance as per the manufacturer's installation instructions must be maintained. In multi-fuel applications and where the flue gas temperature is greater than 250°C, the ventilated fire stop and ventilated support components must be used at the bottom and top of the shaft. For oil and gas applications where the flue gas temperature is below 250°C or where the chimney passes through a non-combustible floor the standard fire stops and support components can be used. No joints can be made within the thickness of any floor or ceiling joists. The twin wall chimney system must project below the ceiling in accordance to the diameter of the flue pipe. (see typical installation)
Use of an adjustable length within the flue pipe connection or twin wall chimney system immediately above the appliance, enables removal of the appliance later without dismantling the full system.
In the room where the appliance is installed, provision should be made for an air vent.This is required to provide adequate air supply to allow the appliance and flue to operate efficiently. These requirements are specified in the Building Regulations. Where a flue passes through an external wall, a wall sleeve must be used.
The size of the chimney system should be as recommended by the appliance manufacturer and in most cases should not be smaller than the appliance outlet. Confirmation from the manufacturer will be required if you reduce the flue size. Flue sizing for commercial applications will depend on individual site details and must be designed and sized in accordance with manufacturer's criteria. For open fireplaces and inglenooks with openings larger than 500mm x 550mm, a flue size with a cross sectional area equal to 15% of the total face area of the fireplace opening will be required. On multi-fuel or wood burning closed appliances of up to 30kw rated output, the minimum flue size must be 150mm internal diameter.
Load bearing supports eg. Wall supports and Ceiling/Joist supports are required to take the vertical weight of a twin wall chimney system. Non load bearing supports eg.wall bands and roof/rafter supports give lateral support throughout the chimney system. Wall bands should be fitted every 3 metres and where the chimney offsets to ensure the system is adequately supported. Where the chimney is free standing above the roof line a height of up to 3 metres can be achieved unsupported with the use of a reinforced or extended locking band at the joint immediately below and every joint above the roof level.
Provision for sweeping, cleaning and maintenance
Provision should be made for inspecting and cleaning the chimney. This is particularly important on solid fuel applications. It is recommended that chimneys serving solid fuel appliances be swept and maintained as frequently as necessary but at least once a year.
The Department for Environment, Food & Rural Affairs (Defra) is seeking information on the use of fuels such as wood, house coal and manufac…
Specflue appoints Deborah McCreadie to Business Development Manager - Commercial Products
HETAS Technical note TN_0022
Specflue's Commercial Director, Ian Sams responds to Sadiq Khan's calls for a Wood-Burning Stove Ban in the capital.
As the air now carries an autumnal nip in the mornings and evening, it will not be long before we experience the first frosts of the season,…
Simple step by step guide on how to check your CO alarm is working correctly and prepare it for the coming heating season.
With just a few days until Christmas, most people should be well into their season of burning with their stoves and open fires. However, the…
Wood needs to dry out and allow the sap to evaporate out of the heart of the timber. Drying wood, although sounding a simple process, has a…
Follow these ten tips to ensure proper installation and avoid some common mistakes.
Schiedel have been manufacturing twin skin flexible liners at their Washington plant for over 40 years and are now proud to offer householde…
The popularity of wood burning appliances has risen in recent years, which means that heating engineers are more likely to be quizzed
While Britain is warming to the benefits of traditional wood burning stoves, Phil Lowe, Head of Sales and Marketing at Specflue, a leading s…